The waste heat generated in the process of industrial manufacturing or refrigeration industry usually needs to be conducted with cooling water. The main function of the square cooling tower is to carry out a heat exchange between the cooling water carrying the waste heat and the air in the tower, so that the waste heat is transferred to the air and dissipated into the atmosphere. The following cooling tower manufacturers will introduce the common problems in the installation of square cooling towers. 1. Cooling capacity issue: Cooling capacity is the core of cooling tower quality. An important component in the installation of the cooling tower - the water spray packing, its function is to reduce the water temperature of the cooling water. The temperature drop produced by the water spray packing reaches 60%~70% of the temperature drop of the entire tower. It can be seen that the quality and performance of the water spray packing To a large extent determines the cooling capacity of the cooling tower. Frequent problems are: cooling tower users find that the cooling effect is not very good during operation, or the water temperature drop of the cooling water is getting worse and worse; or the cooling capacity is completely lost. 2. Water loss problem: The water loss of cooling tower is a water-saving operation parameter worthy of attention. The amount of new water added to the cooling equipment
installation depends on the amount of water lost during the cooling water cycle. The loss of water in the cooling tower includes: evaporation loss, wind blowing loss, and blowdown loss. (1) Evaporation loss. Evaporative losses are inevitable in wet cooling towers. (2) Wind loss. Wind loss refers to the water droplets in the hot and humid airflow discharged from the cooling tower that are drifted out of the tower by the wind. (3) Sewage loss. It should be an important loss. The blowdown loss of a cooling tower is the amount of water that is taken away by discharge from the cooling pool to prevent scaling from dissolved solids. In actual operation, the cooling equipment users have no process guarantee for the stability of the cooling water quality, resulting in a high concentration of cooling water, increasing the amount of sewage and increasing the amount of new water to be supplemented.
Shandong Kehua Intelligent Equipment Co.,Ltd. is trying to institute social good changes this relationship because it averts a firm's resources from its core task of increasing profits.
Shandong Kehua Intelligent Equipment Co.,Ltd. would like to provide our customers with as near perfect protection, as near perfect service as is humanly possible and to do so at the lowest possible cost.'
high frequency induction heating machine induction heating system is characterized by various advantages, such as high frequency induction heating machine, high frequency induction heating machine and high frequency induction heating machine, which is not the case with other induction heating system.
Visit Kehua Electric Furnace to find recent dynamics of induction heating system and contact Shandong Kehua Intelligent Equipment Co.,Ltd. for the latest and most capable in global market.
In various different types of high frequency induction heating machine, high frequency induction heating machine induction heating system is one of the most commonly used.