Industrial towers are also a type of cooling towers. However, some industrial towers are of steel-concrete structure. First, the civil construction is based on the drawings to build the frame, and then the motor, fan blades, filling materials, etc. are installed. The main precautions are basically the same: 1. It should be installed in a well-ventilated place, not in a place with poor ventilation and The moisture return place should not be located in the kitchen and other places where high temperature air is discharged, and keep a certain distance from the heat source such as high temperature exhaust air and chimney, so as not to reduce the effect. 2. When installing, it should be leveled and aligned according to the center position and elevation. The installation of the equipment should be stable and firm. The direction and position of the outlet pipe and nozzle should meet the design requirements. 3. When the counter-flow cooling equipment
uses the rotating water distributor, the holes of the water distributor must not be bent or blocked, and the rotating part must be flexible. The water spout is downward at an angle of 30 degrees to the horizontal plane, and the direction is the same. 4. The cooling tower should be set up in a place with low noise requirements and allowing water droplets to splash. When there are certain noise and temperature requirements, measures should be provided for noise reduction and sound insulation or water droplets splashing or centralized drainage. 5. If multiple cooling towers are installed in parallel, attention should be paid to the unbalanced resistance of the parallel pipelines, resulting in uneven distribution of water components. In order to prevent this problem, a control valve is set on each water inlet pipe to adjust the water volume. 6. The installation site of the cooling tower must be installed at the designated position in the design. Before installation, the compressive strength of the core structure should be affected. If necessary, it should be reinforced according to the design requirements. The installation of the cooling tower should be balanced and firm. 7. When installing a glass fiber reinforced plastic cooling equipment or a cooling equipment with plastic products as fillers, it should be carried out in strict accordance with the fire protection regulations. Generally, flame retardant materials are used for isolation protection.
There are many issues that affect high frequency induction heating machine, which has led to the need of getting specialists trained in certain areas so as to handle all issues that may arise as well as induction heating system products that can solve high frequency induction heating machine problems.
Shandong Kehua Intelligent Equipment Co.,Ltd. are dedicated to providing excellent underwriting and loss control advice up front, and to ensuring superior customer service through the life of the policy.
Before investing in a high frequency induction heating machine induction heating system, it can benefit to have an understanding of the different types of and the most effective strategies to high frequency induction heating machine. Go to Kehua Electric Furnace for more tips.