If the square cooling tower fails, the square cooling tower manufacturer must first determine the cause of the failure, and then solve it in a targeted manner. 1. The cooling tower is equipped with a water-cooled chiller. For the cooling tower using the belt deceleration device, stop and check the tightness of the belt every two weeks. If it is not suitable, adjust it. If the tightness of several belts is different, a full set is required. Replace, if the cooling tower is not running for a long time, remove the belt for storage. 2. If the cooling equipment
uses a gear reduction device, stop the machine every month to check the oil level in the gearbox, and add more oil when the oil is not enough; in addition, the cooling tower should check the color and If the viscosity cannot meet the requirements, it must be replaced; when the cooling tower has been used for 5000 hours, regardless of the oil quality, the gearbox must be cleaned, and the lubricating oil must be replaced, and the lubricating oil must be replaced to ensure that the cooling equipment can provide the chiller. Continuous circulation of cooling water. 3. The motor of the cooling tower fan works in a humid and hot environment for a long time. In order to ensure its insulation performance and no motor burnout accident, a motor insulation test must be done every year; if the requirements are not met, it will not only affect the cooling tower, but also directly affect The water-cooled chiller cannot work properly, so it is necessary to deal with or replace the TV in time. 4. Pay attention to check whether the packing is damaged. If so, repair or replace it in time. 5. The grease of all bearings of the fan system is generally replaced once a year. 6. When using chemicals for water treatment, pay attention to the corrosion of the fan blades; in order to slow down the corrosion, remove the corrosion on the blades once a year, apply anti-rust paint evenly, or paint a layer of 0.2mm thick on the blades of epoxy resin. 7. In winter, the water-cooled chillers in some areas are not in use, and the matching cooling towers will also be shut down. During this period, the fan blades may be deformed due to snow accumulation. At this time, two methods can be taken to avoid: one is to shut down Then rotate the blade to an angle perpendicular to the ground and fix it; one is to remove the blade or even the hub together and store it indoors. 8. When the cooling tower is out of use in winter, when there is a possibility of freezing, it is necessary to say that all the water in the cooling equipment water pan and the cooling water system of the outdoor part is released to avoid freezing damage to the equipment and pipes.
have manifold induction heating system effects, ranging from high frequency induction heating machine to high frequency induction heating machine.
Shandong Kehua Intelligent Equipment Co.,Ltd.’s goal is to provide the customer with an enjoyable, honest service by satisfying individual customers practical transportation needs with a quality product.
can be used in a wide variety of ways.
People tend to want what they perceive they cannot have. Making Kehua seems exclusive or as if it will go out of stock if they don't act quickly often makes it more enticing to the consumer and increases the likelihood that they will buy in.
The lower cost of induction heating system, compared to other product, and Shandong Kehua Intelligent Equipment Co.,Ltd.’s services provide may well suit the needs for customers.