1. The cooling tower is used with a water-cooled chiller. For the cooling tower using the belt reduction device, the belt should be stopped every two weeks to check the tightness of the belt. If it is not suitable, it should be adjusted; ;If the cooling tower is not running for a long time, the belt should be removed and stored. 2. If the cooling tower uses a gear reduction device, stop the machine every month to check the oil level in the gearbox; if the oil is not enough, it should be added in place; in addition, the color and viscosity of the oil should be checked every six months of operation of the cooling tower, up to The ones that are not required should be replaced; when the cooling equipment
has been used for 5000 hours, regardless of the oil quality, the gearbox should be cleaned and the lubricating oil should be changed to ensure that the cooling equipment can provide continuous cooling water for the chiller. 3. The motor of the cooling equipment fan works in a humid and hot environment for a long time. In order to ensure its insulation performance and prevent the motor from burning out, the motor insulation test should be done every year; if it fails to meet the requirements, it will not only affect the cooling tower, but also directly affect the The water-cooled chiller cannot work properly, so it is necessary to deal with it in time or replace the motor. Fourth, pay attention to check whether the packing is damaged, if so, repair or replace it in time. 5. The grease of the bearing of the fan system is generally changed once a year. 6. When using chemicals for water treatment, pay attention to the corrosion of the fan blades; in order to slow down the corrosion, clean the corrosion on the blades once a year, apply anti-rust paint evenly, or paint a layer of 0.2mm thick on the blades of epoxy resin. 7. In winter, the water-cooled chillers in some areas are not in use, and the matching cooling towers will also be shut down. During this period, the fan blades may be deformed due to snow accumulation. At this time, two methods can be taken: one is after the shutdown. Rotate the blade to an angle perpendicular to the ground and fix it; one is to remove the blade or the hub together and store it indoors. Eight, when the cooling tower is out of use in winter, when there is a possibility of freezing, it is necessary to talk about the water in the cooling tower water pan and the cooling water system of the outdoor part, so as not to freeze the equipment and pipes.
Wow, this sounds like a bit of a cruel question, but it is a vitally important question to ask yourself if you are struggling with your high frequency induction heating machine and you would like to stop the induction heating system problem.
Shandong Kehua Intelligent Equipment Co.,Ltd. will continue to bring our industry nuances of style and approaches to induction heating system which are consistent with our evolving aspirations.
To do that, Shandong Kehua Intelligent Equipment Co.,Ltd. will need to make sure our business is listed accurately on as many directories as possible, including technology and quality.
Shandong Kehua Intelligent Equipment Co.,Ltd. provides a way for you to understand your customers, to learn what makes them unique and what motivates their behavior. We can then leverage that wealth of information to personalize our interactions and demonstrate that induction heating system is valuable to our customers.